I am trying to configure an advanced alert to monitor contacts on our APC environmental unit. I configued a Custom Poller using OID 184.108.40.206.4.1.3220.127.116.11.18.104.22.168.2. I can see it is monitoring and registering a 3 on the Node Detail (which it is supposed to while I am testing). It is normally supposed to be a 2.
I have tried to configure an advance alert using one of these methods but can't get it to trip.
OID is equal to 22.214.171.124.4.1.3126.96.36.199.188.8.131.52.2
Numeric Status is equal to 3
I have tried it as Status, Total, Rate - same thing -no alert
I have also tried to use CustomPoller Name instead of the OID - same thing - no trip.
Disregard.... discovered I was using Custom Interface poller by mistake. once I changed to Custom Node Poller it worked.