Has anyone had any luck with a Custom MIB for a TrippLite UPS? I have 3 of these, same models, in a smaller datacenter at a site. I have traps and alerts set fine, but I'd like to be able to monitor Input and Output Voltage, Battery Charge, UPS Status, and Current Load. I walked the device, and received several responses with the info I need, but Solarwinds doesn't seem to get a response. I've tried writing the MIB, as I've done with several other devices, but my attempts seem to have failed.
If anyone has suggesstions (or would like to post a CustomMIBPoller) I would be greatful.
I realize this is an old post.
We have several TrippLite UPSs and are using these pollers. (Thanks grantsewell !) I've also found and added the following poller but it doesn't seem to be supported (OID not supported) by all TrippLites which has me stumped. I'm not sure if it is firmware version related or not. I'm curious if anyone else is using this OID successfully? If not, how you are determining UPS on/off battery status? I've searched through the TrippLite private MIB 126.96.36.199.4.1.850 and haven't been able to find an OID that supports on/off battery status either. Any advice will be greatly appreciated.
If the unit is on battery power , the elapsed time
since the UPS last switched to battery power , or the
time since the network management subsystem was last
restarted , whichever is less. Zero shall be returned
if the unit is not on battery power.
Thanks! Actually, that worked great. I was able to add pollers for everything I needed except for the Output Load. I'll keep searching for that one - I didn't even think to use the generic pollers. Definetely something to try if I have trouble in the future.
SolarWinds solutions are rooted in our deep connection to our user base in the THWACK® online community. More than 150,000 members are here to solve problems, share technology and best practices, and directly contribute to our product development process.