Looking for Liebert UPS mibs. trying to build a report to run, and find bad battery indicators.
Number of current conditions present (like a failed battery test):
Battery test Result:
220.127.116.11.4.1.418.104.22.168.5.1.8 (unknown(1), passed(2), failed(3), inProgress(4), systemFailure(5), inhibited(6))
Estimated minutes remaining:
22.214.171.124.126.96.36.199.2.3 (zero if battery is known bad)
Also note that you could test the battery charge percentage (188.8.131.52.184.108.40.206.2.4). If it doesn't bounce back quickly after an automated battery test, it is getting weak. So alerting on this percentage being below 60% for several hours is a good indicator. (Weak batteries often drop to 50% immediately upon putting a load on the battery during a test or real outage).
SolarWinds solutions are rooted in our deep connection to our user base in the THWACK® online community. More than 150,000 members are here to solve problems, share technology and best practices, and directly contribute to our product development process.